|Place of Origin:||Zhangjiagang,China|
|نام تجاری:||HD BOILER|
|Model Number:||QF 9.5/1050|
|Minimum Order Quantity:||1Set|
|Packaging Details:||Seaworthy Packing|
|Payment Terms:||L/C, T/T, Western Union|
|Supply Ability:||20 Sets / Year|
|Condition:||New||Range of Applications:||Industrial|
|Output:||Steam||Water Circulation:||Natural Circulation|
|Pressure:||Low / Intermediate / High Pressure||Port:||Shanghai|
Heat Recovery Steam Generators (HRSG)
Heat Recovery Steam Generators are a type of Waste Heat Recovery unit which uses waste heat (generally from Gas Turbines) to generate steam. Therefore, HRSGs are generally attached to the exhaust of Gas Turbines. They are commonly used in Combined Cycle Power Plants where both Gas and Steam turbines are used to drive generators. Common parts of a heat recovery steam generator include the following:
• Superheater and desuperheater
• Steam drum, mud drum, drum internals
• Duct Burner for supplemental firing
• Blow down tank
• Firing equipment including duct burner, burner management system, pilot burner
• Bypass stack and exhaust stack, sealing air fan,baffles, piping, valves and controls
1. The design and construction of HRSG should be such that no detrimental vibration of tubes, piping, casing, transition ductwork and exhaust stack is present under any operating condition.
2. All components of HRSG system should be capable of being completely drained. Low point drains should be provided for all enclosures, ducts, piping, and coil assemblies. All drain connections provided on coil assemblies should be piped together to provide a single collection point.
3. Supplementary firing should be adopted as required and can be achieved by duct burners.
4. If designed and constructed to ASME BPVC, the manufacturer should obtain material certificates for all components, and all required code stamps and certificates .
5. Superheater elements should be located and supported to prevent vibration, sagging and misalignment
6. For greater efficiency economizers should generally be furnished as part of an HRSG.
|Cement production line capacity t/d||1000||2500||5000||10000|
|Boiler inlet flow Nm3/h||Kiln(front)||60000||88000||243000||472000|
|Boiler inlet gas temperature℃||Kiln(front)||370||360||380||390|
|Rated evaporation t/h||Kiln(front)||5.8||7.25||24||50|
|Rated steam pressure Mpa||Kiln(front)||1.25||1.25||1.25||1.25|
|Rated steam temperature℃||Kiln(front)||340||330||350||360|
|Kiln(tail)||Vertical||Vertical and Horizontal||Vertical and Horizontal||Vertical
Established in 1985,Zhangjiagang Hua Dong Boiler Co.,Ltd.(trading as HD Boiler),produces power plant; industrial; waste heat; waste incineration; biomass; organic heat carrier and electric steam boilers. Coupled with a comprehensive range of heating surfaces, HD Boiler brings to the market a unique service including boiler design , fabrication, installation, maintenance and replacement of boiler pressure parts.
1. Fabrication area of 400,000 square meters
2. 150 Engineers
3. 600 Coded welders
4. 60 Licensed Inspectors(NDT Level-III instructors)
5. Class-A Licenses for Design and Manufacture Boiler
6. ISO 9001:2008 Quality System
7. ASME Certificate of Power Boilers
8. ASME 'S','U' and NB stamp authorization
تماس با شخص: becky